PROFIBUS dp/v1 fieldbus coupler 12 mbaud digital and analog signals. Part #, Manufacturer, WAGO. GTIN, Condition, New. Quantity . Accessory Type: Fieldbus Coupler. Current Rating: mA. Current Rating: mA. External Depth: mm. External Depth: mm. External Width: 51mm. Hi everyonei’m a beginer and i’m trying to connect wago I/O system with CPU CDP But I Don’t know where i did the mistake i.
|Published (Last):||20 June 2018|
|PDF File Size:||14.92 Mb|
|ePub File Size:||2.74 Mb|
|Price:||Free* [*Free Regsitration Required]|
The modules are configured when projecting the nodes.
The 750-333 responds by returning a maximum of bytes input data to the master. Courier Program code are printed with the font Courier. The current capacity of the power wqgo is 10 A max. Or point us to the URL where the manual is located. The others contain manufacturer specific parameters. Male contacts are located on the left-hand side of the bus modules. Bus connection gd Note When connecting the subscriber ensure that the data lines are not mixed up. Hello karim; Have a look at the Diagnostics section of the manual, the first part shows how to evaluate an error based on the diagnostic LED status: All about Decentral Peripherie.
Display elements 3. Your manual failed to 750-3333 I believe the following link is the one you showed originally; it contains a sample configuration for the as a Profibus slave to a SDP master: Bit Smallest information unit.
A fault in the master can also lead to a fieldbus failure. This channel is allocated to the coupler. Explosive Environments Identification acc. So please open the diagnostic buffer and ry to interpret the errors wgo ee there.
Always plug a bus end module onto the end of the fieldbus node! A fault is cyclically displayed with up to 3 blink sequences.
If you have trouble doing so, Save As Text the contents of the buffer and attach the messages that seem to relate to a bus fault to your next reply, we might be able to help you find the source of the problem with more precision.
Only disconnect the equipment when the power supply has been switched off or the area is known to be a non-explosive area. Parameter Value Wave resistance With diagnosis capable terminals the diagnosis message can be suppressed or released for a channel or module.
The fieldbus line is specified in EN 50 as a line type A and must provide certain line parameters. The slave generates a detailed diagnosis message.
The diagnostic buffer of the S7 CPU should contain messages detailing the source of the problem. Hi dchartier thank you a lot 750-333 all this helpful informations. Any use of this manual which infringes the copyright provisions stipulated herein, is not permitted. The device supply is intended both for the system and the field units. Analog inputs are followed by 2 bytes reserved for future options.
probleme with wago and S CPU CDP – Entries – Forum – Industry Support – Siemens
By the way, the end module is required to terminate the IO bus of the Wago modules, but is not part of the configuration. Self-cleaning power jumper contacts P.
Page Explosive Environments Identification acc. Hello Karim; Please look at the following discussion on the Siemens forum, specially the last one: Don’t see a manual you are looking for? Modules with diagnosis capability allow the diagnosis message to be suppressed or released channel for channel.
During projecting of the inputs and outputs a substitute value can be laid down for each channel. The fieldbus coupler or the process data channel is to be configured on the first slot. This comprises of a header byte, a byte, the channel type and the channel number and a third which describes the fault type and the channel organisation.
Please research this very useful aid when looking for information oin your module. The fieldbus controller or the process data channel is to be configured on the first slot.