CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||10 October 2011|
|PDF File Size:||12.11 Mb|
|ePub File Size:||17.22 Mb|
|Price:||Free* [*Free Regsitration Required]|
Common trouble signal operates. Description Type Model No. F Confirm that the alarm transmission to the fire signal receiving centre is received.
Nozzle is intact with no parts missing? Rechargeable batteries shall not be used in s53 alarms unless specifically recommended by the manufacturer. Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber.
T Output circuit alarm indicators operate.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
For reduced voltage or reduced current starting, record time controller is on first step: Cabinets accessible and identified? Annual Testing – The Annual Test of the fire alarm system is performed by qualified technical personnel to a specific National Standard. There are a total of: Annual Special Inspection Contact Person: Tamper switches inspected covers secured, leaks or corrosion? Plug-in cables securely in place.
Alarm signal silence visual indicator operates. Valve supervisory switches tested? Documents Flashcards Grammar checker. Gauges tested and calibrated or replaced?
Standards Council of Canada
I Terminals clamped tightly. Intelligibility clarity of voice messages confirmed. Are above readings comparable to design values?
Automatic transfer from alert to alarm signal cancel acknowledge operates on a two stage system. Is an AC disconnecting switch installed? Where active and supporting field devices are utilized, device labels correspond with actual field location.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Indicate type of test performed on a fully charged battery select one: All sprinkler u,c regulating control valves passed full flow test? Displays are visible in the installed location. Abnormally frequent false tripping of dry-pipe valves? Fire Alarm System Inspection Services. Check relief port on pressure reducer valves are not leaking? Annual Operate emergency starting means without power Trip circuit breaker if provided?
Have modifications or renovations been done since the last inspection?
Smoke detector alarm verification status change confirmation verified. AA Fire alarm reset function operates.
Ionization type smoke detectors utilize a small source of radioactive material usually Americium that in fact ionizes airborne particulates and attracts them to to one side or the other of a polarized grid. Inspect air pressure and water pressure?